|Outlet Capacity:||2000-50000LPH (Liter Per Hour)||RO Material:||SS,FRP,UPVC|
|Operation:||Automatic Or Manual||Temperature:||4~45℃|
|Feed Water:||River Water,city Water,underground Water||Machine:||2-stage Reverse Osmosis Drinking Water System|
|Sales Service Provided:||Online Technician Support||Certification:||ISO,CE|
50000LPH RO Water Purification Plant,
45℃ RO Water Purification Plant,
ISO9001 RO Water Purification Plant
What is two stage Reverse OsmosisSystem? and how it works?
The term “stage” and “pass” are often wrongly confused as the same thing. It is important to understand the difference between 1 & 2 stage RO and 1 & 2 pass RO.
In a one stage RO system, the feed water enters the RO system as one stream and exits the RO as either concentrate or permeate water.
In a two-stage RO system, the concentrate from the first stage becomes the feed water to the second stage. The permeate water that is collected from the first stage is combined with the permeate from the second stages. Additional stages increase the recovery of the system.
A “pass” shall be seen as a stand alone RO system . The difference between a single pass RO system and a double pass RO system is that with a double pass RO, the permeate from the first pass becomes the feed water to the second pass (or second RO) which ends up producing a much higher quality permeate because it has essentially gone through two RO systems.
Bottled water Filling machine
We have the long-term cooperation partner who produce the filling machine, the Production process includes:
automatic drawing - brush - automatic barrel - disinfection - sterilization - filling - sealing, bagging - transport - finished products
Main Process of Two stage / Double Pass Reverse Osmosis Drinking Water System
XST will design the full Reverse osmosis water treatment plant according to your feed water quality and product requirements. Passes and Stages will be applied when needed. XST will provides sustainable and complete solutions with RO technology, integrating it with the pre-treatment and post treatment necessary.