|Output Flow:||100-15000GPM||Materials:||FRP, UPVC, S.S304/316|
|Turbidity:||＜100NTU||Local Electricity:||220V / 380V / 415V - 50Hz/60Hz|
|Feed Water:||Tap Water, Well Water, Underground Water, Brackish Water...||Membranes:||Dow / Toray/ CSM/ Hydraunics/ Vontron Etc As Clients' Requirement|
|Service Provided:||Online Support,commissioning And Training,Field Installation,Video Technical Support,Field Maintenance And Repair Service||Certification:||ISO9001, CE|
RO Brackish Water Treatment Plant,
UPVC Brackish Water Treatment Plant,
10000GPM Water Purification System
Description of RO Brackish Water Treatment Plant
Reverse osmosis is a water purification technology that uses a semipermeable membrane to remove larger particles from drinking water. It differs from filtration in that the mechanism of fluid flow is by osmosis across a membrane. The predominant removal mechanism in membrane filtration is straining, or size exclusion, where the pores are 0.01 micrometers or larger, so the process can theoretically achieve perfect efficiency regardless of parameters such as the solution's pressure and concentration. Reverse osmosis instead involves solvent diffusion across a membrane that is either nonporous or uses nanofiltration with pores 0.001 micrometers in size. The predominant removal mechanism is from differences in solubility or diffusivity, and the process is dependent on pressure, solute concentration, and other conditions. Reverse osmosis is most commonly known for its use in drinking water purification from seawater, removing the salt and other effluent materials from the water molecules
The Brackish Water Treatment System is belong to Reverse osmosis (RO) system, which the inlet water quality is a little worse, which the TDS may be more than 2000mg/L, and it needs the higher standard of materials when we make the design.
Main Process of RO Brackish Water Treatment Plant
1. feed water pump pump-- provide the pressure to quartz sand filter/active carbon filter
2. Multi-medium filter-- get rid of turbidity, suspended matter, organic matter, colloid, ect.
3. Active Carbon filter--Remove the color, free chloride, organic matter, harmful matter, ect.
4. Softener--exchange "ions" of calcium and magnesium with the most common and easiest method.
5. Security filter--prevent large particles, bacteria, viruses into RO membrane, accuracy is 5um
6. High pressure pump-- Provide the high pressure to RO membrane
7.Brackish water treatment system-- main part of the plant. The RO membrane's desalting rate can reach 99%, removing over 99% ions
Pictures of RO Brackish Water Treatment Plant
Maintenance of RO Brackish Water Treatment Plant
Replacement time of consumable parts
There are several kinds of consumables you need to replace regularly.
a. Quartz sand: replaced about every 15-18 months. 50kg/bag
b. Activated carbon: replaced about every 15-18 months. 25kg/bag
c. Resin: replaced about every 15 months. 25L/bag
d. PP Filter cartridge: replaced about every 3 month
e. RO membrane: replaced about every 2years
We suggest customers buy 1- 2 years of PP filter cartridges together with machine. Because these PP filter cartridges need to be replaced every month.